|Type:||Floor Heating Parts, Floor Heating Systems, Floor Heating Thermostats, Bat-low Indicator, HVAC Systems||Floor Heating Part Type:||Floor Heating Thermostats, Floor Heating Cables, Floor Heating Panels, Under Flooring Heating System|
|Application:||Underfloor Heating System, Water Heating/Electric Heating System/Boiler, Indoor Underfloor Heating, Electric Underfloor Heating System.Radiant Heating Room Thermostat, Water Heating System||Certifications:||CE, ROHS|
|Material:||PC+ABS||Usage:||Household, Underfloor Heating Controls System, Bolier Temperature Controller, Gas Boiler, Underfloor Water Heating|
Alkaline Batteries Wired Room Thermostat,
Wired Room Thermostat With Backlight,
Non Programmable Thermostat With Backlight
Heating / Cooling Non-Programmable, With Backlight Room Thermostat S2305
2.Display Temperature Range:3°C~37°C (in 0.1°C increments)
3.Adjustable Temperature Range:5°C~35°C (in 0.5°C increments)
4.Temperature measurement accuracy: ±1°C (at 20°C)
5.Defrosting Temperature: +7°C
6.Power source: 2x AAA 1.5V Alkaline Batteries
7.Load Rating: 6(2)A, 230V
8.Low Battery Indicator: Display ““ when battery is less than 2.7V
10.Backlight colour: Orange / Blue
11.Dimensions: 122 x 76 x 25 mm
1. HEAT SWING: Hold + and - under the “HEAT”mode for 3 secs to enter the interface of Swing setting (in 0.2~2); Press + or - to set the desired value,then wait for 15 secs for auto confirmation.
2. COOL SWING: Hold + and - under the “COOL”mode for 3 secs to enter the interface of Swing setting (in 0.2~2); Press + or - to set the desired value, then wait for 15 secs for auto confirmation.
1. Press RESET to reset the thermostat (turn off then turn on the power, the settings won’t be changed).
2. Hold -, then press RESET to restore the factory default settings.