|Place of Origin:||China|
|Minimum Order Quantity:||500pcs/model|
|Packaging Details:||Standard exporting package|
|Delivery Time:||7-50 working day|
|Payment Terms:||T/T, Western Union, MoneyGram|
|Floor Heating Part Type:||Under Flooring Heating System||Application:||Water Heating/Electric Heating System/Boiler|
|Type:||Floor Heating Parts, Floor Heating Systems, Floor Heating Thermostats, Bat-low Indicator, HVAC Systems||Certifications:||CE, ROHS|
|Usage:||Household, Underfloor Heating Controls System, Bolier Temperature Controller, Gas Boiler, Underfloor Water Heating||Feature:||Save Energy|
Wired Non Programmable Thermostat,
LITHIUM BATTERY Non Programmable Thermostat,
1.5V LITHIUM BATTERY Wired Room Thermostat
2.Display Temperature Range:0°C~40°C (in 0.1°C increments)
3.Adjustable Temperature Range:5°C~35°C (in 0.5°C increments)
4.Temperature measurement accuracy: ±1°C (at 20°C)
5.Defrosting Temperature: +7°C
6.Power source: 2x AAA 1.5V LITHIUM BATTERY
7.Load Rating: 6(2)A, 230V
8.Low Battery Indicator: Display ““ when battery is less than 2.7V
10.Backlight colour: Orange / Blue
11.Dimensions: 118 x 80 x 26 mm
Heating: connect the two connection wires of the device to be controlled to terminals No. 3 (NO) and No. 2 (COM), i.e. to the normally open terminals of the relay
Cooling: the two connection wires of the cooling equipment should be connected to terminals No. 2 (COM) and No. 1 (NC), i.e. to the normally closed terminals of the relay.
• To prevent electric shock, replace the inner cover removed for the connection of wires after the assembling process has been completed.
The device must be installed and connected by a qualified professional. Always follow the manufacturer's instructions when connecting the thermostat to any heating or cooling appliance.
The voltage appearing at terminal No. 1, No. 2 or No. 3 depends only on the system being controlled, therefore the dimensions of the wire are determined by the type of the device to be controlled. The length of the wire is of no significance.
Switch by press in different mode:
HEAT (Heating): adjust the temperature by press + or -
COOL (Cooling): adjust the temperature by press + or -
OFF (Frost Protection): it will start heating when the room temperature is under 7°C
1. HEAT SWING: Hold + and - under the “HEAT”mode for 3 secs to enter the interface of Swing setting (in 0.2~2); Press + or - to set the desired value, then press to confirm.
2. COOL SWING: Hold + and - under the “COOL”mode for 3 secs to enter the interface of Swing setting (in 0.2~2); Press + or - to set the desired value, then press to confirm.
3. Calibrate the temperature: Hold + and - under the “OFF”mode for 3 secs to enter the interface of temperature