1.5V Alkaline Batteries LCD Display Smart Home Digital Room Thermostat For Heating / OFF / Cooling
|Place of Origin:||CHINA|
Payment & Shipping Terms:
|Minimum Order Quantity:||1PC|
|Packaging Details:||Carton box|
|Delivery Time:||7-30 days|
|Payment Terms:||L/C, D/A, D/P, T/T, Western Union, MoneyGram/Paypal|
|Supply Ability:||60000 pieces/month|
|Product Name:||Digital Temperature Controller||Stages::||1 Heat/1 Cool|
|Body Color::||White||Power Supply::||230V,50HZ|
|Warranty::||One Year||Dimensions::||130 X 86 X 35 Mm|
digital air conditioner thermostat,
digital furnace thermostat
LCD Display Smart Home Digital Room Thermostat For Heating / OFF / Cooling
Room Temperature Calibration adjustment
Power supply: 230 VAC,6(2)A,50/60 Hz for hardwire (common wire)
2*AAA 1.5V Alkaline batteries power
|1||Product Name:Color Touch Heating Thermostat|
|3||Display temperature range:0°C~40°C (in 0.1°C increments)|
|4||Setpoint Range:5°C~35°C (in 0.5°C increments)|
|5||Temperature measurement accuracy:±1°C (at 20°C)|
|7||Power Method:2 x AAA 1.5V Lithium batteries|
|8||Dimensions:130 x 86 x 35 mm (without holder)|
|9||Running Mode:HEAT/OFF/COOL MODE|
|10||Load Rating: 6(2)A, 230V|
|11||Standby current: <70uA, Lighting current ≤7.2mA|
Heating: connect the two connection wires of the device to be controlled to terminals No. 3 (NO) and No. 2 (COM), i.e. to the normally open terminals of the relay
Cooling: the two connection wires of the cooling equipment should be connected to terminals No. 2 (COM) and No. 1 (NC), i.e. to the normally closed terminals of the relay.
• To prevent electric shock, replace the inner cover removed for the connection of wires after the assembling process has been completed.
The device must be installed and connected by a qualified professional. Always follow the manufacturer's instructions when connecting the thermostat to any heating or cooling appliance.
The voltage appearing at terminal No. 1, No. 2 or No. 3 depends only on the system being controlled, therefore the dimensions of the wire are determined by the type of the device to be controlled. The length of the wire is of no significance.
Hold the dial button for 5 seconds to access the system running mode switch, then turn the dial to choose different mode between:
-- HEAT (Heating): adjust the temperature by turn the dial
-- COOL (Cooling): adjust the temperature by turn the dial
-- OFF (Frost Protection): it will start heating when the room temperature is under 7°C
Then press the dial again to confirm the running mode or wait for 10 seconds to confirm the setting automatically.
Calibrate the temperature
Temperature calibration and SWING settings): Hold the dial for 5 seconds to access to the mode switch setting and select HEAT or COOL mode, then press the dial to access the interface of temperature calibration “CAL” (in -3.0~+3.0, in 0.5°C increments); turn the dial to set the desired value, then press the dial again to set the Swing value between 0.2~2°C.
Restoring thermostat to factory default
Remove the batteries then put it back, hold the dial until display the full screen then release, the defaul running mode is HEAT, it means the thermostat has been restored to factory default settings.